Tankalert Eco Oil
|TANK||Min. 0,5 m (depth) - Max 3 m (depth or wide) Max 19.999 litres - Min 300 litres (content)|
|MEASUREMENT DISPLAY||Multi-function LCD display including: -- 10 bar-graph level indication on both Inpro EcoOil Monitor and Transmitter* --Display of various current and historical values --Display control with five control buttons. --Red LED for low level indication at 5% or less of usable fuel remaining. -- Audible alarm sounds every hour on the hour when the tank level is low. * The transmitter and Monitor bar-graph displays may differ (see display symbol reference table).|
|MAX COMUNICATION DISTANCE||Typically 150m in normal ‘line of sight’ conditions|
|POWER SUPPLY||Receiver: --Mains Power Supply (included): 150V-240V, 50-60 Hz, meets EN60950-1. (5V DC (40mA)) --Back up battery**: 3V LiMn ** This device contains a small battery to keep time during power cuts. If the device is left unpowered for an extended period then the battery will deplete.|
|BATTERY LIFE||Transmitter: 5 years (estimated life)|
|WIRELESS COM||433MHz FM transmission (EN300-220)|
|DIMENSIONS||Receiver: 120mm x 90mm x 50mm Transmitter: 140m x 70mm x 40mm|
|MAX AND MIN OPERATION (TRANSMITTER)||Operating temperature range: -10°C to +60°C Operating Humidity : 0 -95% non-condensing|
|HOLE SIZE FOR TANK FITTING||60 mm or 2”, 1½”, 1¼”, thread|
What should I do if the reading received is unintelligible? E01
Check that the transmitter is in a vertical position within the tank (making sure that the transmitter is not too close to the sides of the tank or to any internal obstructions). − Ensure that the transmitter is not too tight on the tank. − Ensure that the tank is not overfull and that the bottom part of the transmitter is clean.
What should I do if no reading is received after 6 hours? E02
Check that the transmitter is within reach of the display. Try placing the display somewhere that is closer to a window, remember that the transmitter and the display communicate through FM signal and moving the plug away from any potential metallic obstruction may improve the signal. − Check that there are no metal objects, such as vans or lorries, or that there is nothing within the structure of the building that could deflect the signal. Wait for an hour to see if the new reading arrives. − Ensure that the display is not too close to, or obstructed by, other electrical devices.
Why is a null reading received? E03
Check the positioning of the transmitter (ensure that the transmitter is not too close to the sides of the tank or to any internal obstructions). − Ensure that the transmitter is not too tight on the tank. − Ensure that the tank is not over-full, that is, that there is at least 12 cm from the liquid to the transmitter. − Ensure that the lower part of the transmitter is clean. − If the tank is double-walled, ensure that the transmitter is placed on the internal tank.
What should I do if I receive a reading that is greater than the height of the tank? EO4
Check the height of the tank and check that the information on the screen is correct, press the keys at the same time to view the tank configuration. If the height in incorrect, press and hold SETUP for 3 second to go to the configuration mode, press ENTER until you reach the screen 5 and adjust the height using the and keys. Press ENTER to save. Press SETUP to exit from the configuration mode. Wait 3 hours for an updated reading. Check that the plugs are configured correctly. − Check that the transmitter is vertical and check its positioning (ensure that the transmitter is not too close to the sides of the tank or any internal obstructions).
What should I do if I get an EO5 or EO6 error?
These are hardware errors and you will need to contact the provider